After a thermal analysis , the ‘Section factor’ can be requested in the data table . But this value does not correspond to section factors that you can find in (most) tables (such as this one).

This is because Diamonds shows the shadow factor k_{sh} multiplied by the section factor A_{m/V}.

Example: IPN 80 (b=42mm; h=80mm; t_{w}=3,9mm; t_{f}=5,9mm, r=3,9mm)

- The perimeter V of the cross-section equals:
- The area of the cross section per unit of length equals A
_{m} - The are of the bounding box of the cross-section pr unit of length equals A
_{m.box} - The shadow factor k
_{sh}then equals (EN 1993-1-2 equ. 4.26a) - The section factor A
_{m/V }(EN 1993-1-2 Table 4.2): - The result shown in the data table of Diamonds in the column ‘Section factor’ equals:

The choice to show the product of the shadow factor k_{sh }and the section factor A_{m/V }has several reasons:

- On the one hand, Eurocode allows the use of the shadow factor when working with nominal fire curves (EN 1993-1-2 §4.2.5.1) (which is almost always the case in Diamonds). By already including this multiplication in the ‘section factor’ column, there is no discussion for the end user that the shadow factor will be charged.
- On the other hand, there are several manufacturers of fire-resistant paints whose data is based on a k
_{sh }x A_{m/V}, which makes the interpolation of the results a lot easier for the calculation core. - Some tables also include the shadow factor like this one.